Ranipet, 2013 to 2016, Repeat jobs.
Was facing CNC and UPS electronics card failures, lighting ballast, and motor burning issues and in addition voltage sag (fluctuation) tripping for CNC m/c. Local Utility company/ TNEB mandated limiting harmonics at it 11kv incoming PCC.
Installed 1011A Tuned harmonic filter, mitigated harmonics within IEEE 519 norms, and eliminated all failures. Further recommended solutions for electronic failures of Chiron high speed CNC drives during its regeneration cycle, connected at UPS output.